|Radiant Section Design
|Convective Heat Transfer In The Radiant Section
|Heat Balance In The Radiant Section
|Radiant Section Rating
|qr = Radiant heat transfer, Btu/hr
|s = Stefan-Boltzman constant, 0.173E-8 Btu/ft2-hr-R4
|a = Relative effectiveness factor of the tube bank
|Acp = Cold plane area of the tube bank, ft2
|F = Exchange factor
|Tg = Effective gas temperature in firebox, °R
|Tw = Average tube wall temperature, °R
Because the tube bank does not absorb all the heat radiated to the cold plane, an absorption effectiveness factor, a, can be used to correct the cold plane area, depending on the arrangement of the tubes. The relative effectiveness factor can be described by the following curves:
For a single row in front of a refractory wall, use Total One Row. For two rows in front of a refractory wall, use Total Two Rows. For double sided firing, use Direct One Row.
The normal heat-absorbing surfaces in a fired heater consist of a number of parallel tubes. In the case of a fired heater design where the tubes are fired from one side only, the tubes are normally positioned in front of a refractory wall. Part of the radiation from the hot gas strikes the tubes directly, while the rest passes through and is radiated back into the chamber, where part is absorbed by the tubes. In the case of tubes fired from both sides, as when the tubes are positioned in the center of the chamber, the tubes absorb direct radiation from both sides. Expressing the tube area as an equivalent plane area simplifies this calculation. The calculated cold plane area is the area of a plane through the tube center lines, whether they are in a curved plane, such as in a cylindrical pattern or in a row side-by-side. For most tube panels, the width would be equal to the center/center spacing of the tubes times the number of tubes. The length is the length of tube exposed to the radiation. In the case of tubes penetrating a tube sheet it is the length between tube sheets. But for tubes with the return bends inside the firebox, the length may be taken as the distance from the centerline of the return on one end to the centerline of the return on the other end.
For a firebox with the tubes down the center, or other pattern which results in the tubes being fired from both sides, the cold plane area would be twice the projected area.
|For single sided firing:
Acp = Ntube*Stube*Ltube
For double sided firing:
Acp = Ntube*Stube*Ltube * 2
Ntube = Number of tubes wide
Stube = Tube spacing, ft
Ltube = Effective tube length, ft
Because the flue gas in the firebox is a poor radiator, the equation must be corrected using an exchange factor which is dependent on the emissivity of the gas and the ratio of refractory area to cold plane area. Since the radiant heat is reflected back into the firebox, by the refractory, a heater having a larger ratio of refractory surface relative to the tube surface, will absorb more heat. Since the tubes themselves are not perfect absorbers, the curves are based on a tube-surface absorptivity of 0.9. This is a value considered typical for oxidized metal surfaces. The overall radiant exchange factor, F, can be taken from the curve below as presented by Mekler & Fairall in Petroleum Refiner, June 1952.
The equivalent cold plane area,aAcp, is the product of the effectiveness factor and the cold plane area as described above. The Aw can be described as follows,
|Aw = Ar - aAcp
|Aw = Effective refractory area, ft2
|Ar = Total refractory area, ft2
|aAcp = Equivalent cold plane area, ft2
The gas emissivity can be described by the curve presented by Lobo and Evans, at AICHE, 32nd Annual Meeting, November 1939. The tube wall temperature has only a minor effect. Therefore, the emissivity can be correlated as a function of PL product and the gas temperature, Tg. Variations in tube wall temperatures between 600 and 1200°F cause less than 1% deviation from these curves.
|Product of the Partial Pressure of the carbon dioxide and water times the Beam Length, in atm-ft.
|For Box Type Heaters
|Mean Beam Length
|1-1-1 to 1-1-3
1-2-1 to 1-2-4
|1-1-4 to 1-1-inf
|1 x Smallest Dimension
|1-2-5 to 1-2-inf
|1.3 x Smallest Dimension
|1-3-3 to 1-inf-inf
|1.8 x Smallest Dimension
|With the box dimensions, length, width, and
height being in any order
|For Vertical Cylindrical Heaters
|Length/Diameter < 2
|(((L/D)-1)*0.33 + 0.67)*D
|Length/Diameter >= 2
For a radiant section that is considered "well mixed", this temperature is assumed to be equal to the temperature leaving the radiant section, i.e., the bridgewall temperature. For most applications, this is an acceptable assumption. But in a high temperature heater with a tall narrow firebox and wall firing, the Tg controling radiant transfer may be 200 to 300 °F higher than the exit temperature. Tall, bottom fired cylindrical heaters are somewhere in between normal and this extreme. For those cases where this is true, either an adjustment such as using another temperature in this equation while using the exit temperature for the heat balance or dividing the radiant into zones for the balance calculations, should be considered.
Average tube wall temperature, Tw
Tube wall temperature depends on the temperature of the process fluid and its transfer coefficient inside the tube, the thermal resistance of the tube wall, the heat flux, and the fouling. The calculation of this temperature will be treated in another section of this guide.
The average tube wall temperature as used herein, may be one of either the average temperature of the front 180° face of the tube, or the overall average for the full circumference. Some engineers follow one method while the others go the other way. Either way, the overall difference between methods is relatively small.
|qc = Convection heat transfer, Btu/hr
|hc = Film heat transfer coefficient, Btu/hr-ft2- °R
|At = Area of the tubes in bank, ft2
|Tg = Effective gas temperature in firebox, °R
|Tw = Average tube wall temperature, °R
This value cannot be calculated precisely, and is usually selected by experience or rule of thumb. The arrangement of the tubes as well as the firebox design contributes to this factor. For horizontal tube, cabin type heater, which is normally small in size, this coefficient might = 1.5, where on large box heaters with multiple tube cells, it may be as high as 2.8. Vertical heaters with an L/D less than 2 would normally be designed with hc = 2, where for an L/D greater than 2.0, you could use 3.0.
The total heat absorbed by the radiant section tubes, now can be expressed by the following equation.
|qR = Total heat transfered to radiant tubes, Btu/hr
|qr = Radiant heat transfer, Btu/hr
|qc = Convective heat transfer, Btu/hr
The procedures we have reviewed above gives us a method to either compute the heat absorbed, or we can calculate the temperature we would need to transfer a specific amount of heat into our process coil. For us to make a heat balance, we will need to determine the firing rate necessary to maintain that temperature. This is accomplished by a heat balance around the fire box.
There are three primary sources of heat input to the radiant section, the burner release, qrls, the sensible heat of the combustion air, qair, and the sensible heat of the fuel and any atomizing medium, qother. Heat is taken out of the radiant section by the two heat transfer methods previously explained, qR and qS, and by losses through the casing, qloss, and sensible heat of the exiting flue gas, qout.
We can now set up the heat balance equation as follows:
|qrls = Heat released by burners, Btu/hr
|qair = Heat in the combustion air, Btu/hr
|qother = Heat in other items, Btu/hr
|qR = Heat absorbed by radiant tubes, Btu/hr
|qS = Radiant heat to shield tubes, Btu/hr
|qloss = Heat loss through setting, Btu/hr
|qout = Heat in gas leaving radiant section, Btu/hr
The burner release can be easily calculated for a gas when we know the composition of the fuel and the heating values of the various components. For liquid fuels, the heating values are obtained by a calorimeter test.
From these values and using the standard combustion equation, we can determine the composition of the flue gas. As an example, the combustion of methane could be stated :
The heat available in the combustion air, such as from preheated air, or using Gas Turbine Exhaust, etc., is taken as the heat content above 60 °F, since that is the design datum temperature for fired heaters. For the purpose of this discussion, radiant heat transfer, we are not going to take this into account, i.e., we will consider the air at 60 °F.qother = Heat in other items, Btu/hr
The heat available in other items would include such things as the fuel when it is above 60 °F, atomizing air or steam, etc. These must be taken into account in heater design, however, for the purposes of these discussions, we are not going to include them.qloss = Heat loss through setting, Btu/hr
Since the flue gas composition remains consistent for a given fuel and excess air, the first thing we need to do is perform the combustion calculation. This is what we did above to compute the burner release. The enthalpy for a given temperature can now be calculated by obtaining the enthalpy for each component and adding them together. And, as with the combustion calculation, this can be done by using a simple computer program. To try this out, click the button below:
Heat Absorbed, Btu/hr = 9,500,000
Tube Wall Temperature, °F = 600
Fuel(Previous example fuel) = Gas
Excess Air, % = 15
Tube Diameter, in = 4.500
Tube Spacing, in = 8
Tube Effective Length, ft = 26.000
Number Of Tubes = 30
Area Of Flue Gas Exit, ft2= 42
Radiant Arrangement = Box
The first thing we notice with this answer is that it doesn't match the hand calculated value. This is because the curve fit to facilitate all the table conditions and those in between, will not give the same value as we get when we select one formula or the next, with no transition. But, the calculated value is fine for our heat transfer calculations.
The emissivity curve requires that we know the Tg, which we don't know at this time. So for these calculations, we are going to initially assume this to be 1500° F. But, as above, we can now interpret the complicated emissivity curve with our browser.
Of course, this is far short of the 9,500,000 Btu/hr heat transfer that we needed to satisfy our process requirement. Experience would have caused us to recognize that we would have needed more surface to achieve a low exit temperature, i.e., bridgewall temperature of 1500 °F. This is a good time to introduce a new parameter, flux rate, into the discussion. The flux rate is a measurement of how hard heat is being pushed into the tubes. It is a criteria used by equipment users to tell a designer limits that he wishes to impose on the design.
|Fluxrad = Radiant tube flux rate, Btu/hr-ft2
|qR = Total radiant heat transfer, Btu/hr
|Srad = Total radiant tube surface, ft2
For our example, the required flux rate is 10,339 Btu/hr-ft2, which is a fairly average flux rate, neither high, 18,000 Btu/hr-ft2, nor low, 6,000 /hr-ft2, for the range that direct fired heaters would generally fall in. A better guess for our exit temperature, would have been 1600 °F to 1650 °F. As you can see, the problem of doing this balance by hand is complicated. And, in the real world, it would be even more so, since the tube wall temperature, and tube process outlet temperature, inlet process pressure, etc., would have to be considered also.
So, lets open another window and do some calculations. Make some changes in the inputs and look closely at the results.
Now we need to review the overall heat balance equation again.
For these examples, the combustion air is at 60 °F, so the qair factor drops out of the equation. The fuel is gas, so there is no atomization and we are assuming it to be at 60 °F, so the qother factor also drops out of the left hand side. On the other side, we have no shield so the qS drops out.
The equation can now be simplified to,
As mentioned above, the qloss is an allowance, and for this example, we can set it to be equal to 1.5% of the burner release, so,
Now we can restate, qrls in other terms,
|Wfuel = Fuel flow rate, lb/hr
|Lhvfuel = Lower heating value of the fuel, Btu/lb
And we can restate, qout in the following terms,
|RatioAirFuel = Air to fuel ratio, lb/lb
|Enthfg = Enthalpy of flue gas, Btu/lb
You will notice that all of these variables, we have a value for, except the amount of fuel, Wfuel. So it becomes a very simple matter to rearrange the equation and solve it for the amount of fuel required to maintain the Tg, that we determined we needed in the previous calculation.
Then, rearranging the equation, it becomes,
Substituting the values we developed earlier,
So the burner release and the flue gas flow,
And, what we really wanted to know, the efficiency of the heater,
This concludes the review of Radiant Section Design, but the following script will provide a window where all of the formulas can be tested for various designs.
The formulas and correlations presented herein are all in the public domain and are to be used only as a learning tool. Note that any product, process, or technology in this document may be the subject of other intellectual property rights reserved by sponsors or contributors to this site. This publication is provided as is, without any warranty of any kind, either expressed or implied, including, but not limited to, the implied warranties of fitness for a particular purpose, or non-infringement.
The formulas, correlations, and methods presented herein should not be considered as being recommended by or used by the sponsors of this site. The purpose of this site is educational and the methods may or may not be suitable for actual design of equipment. Only a fired heater design engineer is qualified to decide if a calculation or procedure is correct for an application.